High Pressure and Low Pressure welding. We also weld hot-taps into existing live piping when shutdown is NOT an option.
We've gone through a lot of analyzers in our time - from Bacharach to UEI. We know COMBUSTION!
Maximizing your boiler's performance with new linkage-less controls. Replacing or adjusting old controls for better performance.
Repairing or replacing old piping. Or installing certified high pressure and low pressure systems.
Removing old refractory and installing more effective and durable refractory in your boiler.
Send specifications to Hobbs and we will fabricate your custom parts.
Let Hobbs know the capacity and the pressure rating as well as the other specifications you will need and we can make up a custom fitted tank for your needs.
A turn key business performing complete retrofitting of your old equipment- removing your old equipment and installing new. Let Hobbs take care of the contracting.
Thermal balancing is better than before. Large single pump systems are history.
Correct sizing and Variable Frequency Drives save a lot of electricity.
Venting & Stack
Correct venting is very important.
Hi- temp wiring may be required.
Natural gas, Propane, Biogas and Oil Conversions
Some burners are better than others, with an upgrade you can save money!
The newer electronic Flame SafeGuards are more reliable and now last longer.
Level Controls, Pressuretrols, Safety valves etc
We Fully Recommend Scheduling Annual Maintenance!
Like most equipment, your boiler should get annual maintenance.
Without an annual tune-up and inspection, small issues can escalate to become serious (and expensive) problems.
What is generally involved in our annual maintenance?
-Open front and rear doors. Clean and vacuum fireside surfaces as required.
-Inspect all refractory. Patch and wash coat as required.
-Inspect all gasketing on front and rear doors and replace as necessary.
-Seal and close front and rear doors properly.
-Remove low and auxiliary low water cut off controls, clean and inspect. Then re-install using new gaskets.
-Remove plugs in control piping, inspect, clean and re-install.
-Remove all hand hole and man hole plates. Flush boiler with water to remove loose scaled and sediment.
-Replace all hand hole and man hole plates with new gaskets.
-Open feedwater tank manway, inspect and clean as required. Replace manway plate with new gasket.
-Clean burner and burner pilot.
-Check pilot electrode and adjust or replace.
-Clean air damper and blower assembly.
-Clean motor starter contacts and check operation.
-Make necessary adjustments to burner for proper combustion and record all results in service report.
-Perform all flame safeguard and safety trip checks and record results in service report.
-Check all hand hole plates and man hole plates for leaks at normal operating temperatures and pressures.
-Troubleshoot any boiler system problems as requested by on-site personnel.
Many boilers today are very old. While these units may still be operational, they may be costing you more money than value.
Some of the issues associated with older boilers can be high gas consumption, high emission levels, low reliability, potential leaks, and noisy operation. A new boiler can fix all of these issues so you can have worry-free operation with no down time. Replacing an existing boiler is not always as simple as just changing out the unit. There are a lot of other considerations that need to be taken into account.
- Is the circulation pump adequate to get water where it needs to go?
- Does the system meet code with a low water cutoff switch?
- Is there an automatic water feed?
- Is there an air eliminator to keep air out of the system?
- Is the expansion tank adequate for the new system?
...and many more!